The connection of contactors and emergency stop buttons is supported. Define the normal state (normally open / normally closed) of the button in the web interface of your alarm system. Then you define the desired actions (relay switching, siren etc.) and alarm messages (SNMP, e-mail, SMS) in the web interface.
Every Didactum Monitoring System is equipped with I / O contacts. Connect the remote monitor to the emergency shutdown of your UPS system using a two-wire cable. If the smoke detector detects a fire, the monitoring unit can automatically switch off the UPS system via a relay circuit. The rule can be easily mapped in the built-in logic. Of course, the I / O contacts can also be switched manually in the easy-to-use multilingual web interface.
Please go to the entry "System menu" in the WebGUI (bottom left). In the "Export" tab, click on "Save log to disk" to export the syslog of your remote monitoring unit. Then go to "Download current settings" and click on “OK”. In the new window "Select settings" please leave all check marks set and then click on "OK". Please send the two files named "Syslog.txt" and "settings.zor" to the support staff by e-mail. If you have received a ticket number, please always state it in the subject line of your e-mail. This will speed up the processing of your support request.
The Ethernet-based remote monitoring units of the model series 50 / 100 IV (DC) / 400 /500 II (DC) permit an physical operating environment from -10 ° C to max. + 85 ° C (14° F to 185° F) at 5% to max. 95% relative humidity (non-condensing). Each Didactum remote monitoring system is equipped with an onboard temp sensor for temperature measurement and monitoring inside the metal case. If the maximum permissible operating temperature is exceeded, you can be notified via SNMP trap, e-mail and / or SMS (via GSM / LTE modem or e-mail SMS gateway). Optionally, the alarm siren including LED flash lights can be connected to the main monitoring unit to report the critical operating temperature.
To display the measurement diagrams in the webGUI, simply click on the "+" sign in the upper left corner. A new window will appear with the sensors connected to your networked remote monitoring unit. Then select the desired environmental sensors and then click on "ok". The measured data will then be displayed graphically immediately. The screenshot below gives you more information.
Of course you can reset your remote monitoring device to default settings. Please download the latest firmware tool here:
In the packed zip file, you find another packed zip called „tools.zip“. Please unpack it and you will find these three tools:
factory-settings.zor – this file is used to restore your Didactum remote monitoring unit to factory defaults. After installing it, your device has default IP adress 192.168.0.193 with default gateway 192.168.0.1
Default user is „guest“ and default password is „guest“ (each without quotation marks). All sensor settings are reset to default settings. Of course you can upload your backup settings.
network-settings.zor – this file is used to restore default network settings of your networked monitoring unit. The default IP address is: 192.168.0.193. Default gateway is 192.168.0.1.
resetusers.zor – With this file, the users of your IP based remote monitoring device are reset to default settings. This is useful if you have lost the password of your Didactum monitoring unit. By installing this file, the default user is „guest“ and default password is „guest“ (no quotation marks).
Please copy the needed file in the root on an empty USB flash drive. Please make sure, that no other than the needed file is on the USB flash drive. Please remove power of your Didactum remote monitor and connect the USB flash drive to USB port on front panel. Connect power again to your monitoring unit.
Please wait while the contents of drive will be analyzed by the monitoring device. The recovery process is indicated by LED on the front panel of the remote monitoring unit. After reboot (all the LED lights go out), please remove USB flash drive.
Important: After installing the recovery file, you have to empty your browser`s cache.
If you have questions, please contact our support via e-Mail to support(at)didactum.com
Please check if you are using a web browser such as Chrome, Firefox or Safari. Furthermore, please check if the latest Java plug-in is installed on your computer.
Please delete the cache and then start your web browser again. Then please enter the IP address of your Didactum remote site monitoring device in the browser field.
The login screen of your Didactum monitoring system will now appear.
Each environmental monitoring system is tested up to 6 days by a comprehensive burn-in procedure. Please check whether the DIP switch (see point 7 on the graphic) is on „Normal" position. If this is not the case, please replace the jumper with a ballpoint pen. After that, your remote monitoring unit should work properly.