We have an Environmental Monitoring System from Didactum in use and want to update the firmware. How can we check which model we are using and which microcode firmware is installed?
Simply log in to your monitoring device via web browser. Go to the menu item "Overal Stats". The entry "About system" will display you the device type and installed firmware version of your environmental monitor.
How can I reset my Didactum Environmental Monitoring System to default factory settings?
In order to restore your Didactum Environment Monitoring System (connected to the power supply) to the default delivery state, you only need to jumper the DIP switch to the recovery position. All individual settings will be permanently deleted. After 15 seconds, please return the DIP switch to the normal position. The environmental monitoring device is then reachable under the default IP address "192.168.0.193". The login is "guest" / "guest". Then you can restore the backup of your configuration. Alternatively, you can "refuel" your Didactum Environmental Monitoring System using the CPU-tool included in the firmware file.
I uploaded the latest Didactum firmware into my environmental monitor via web browser. After installing the FW update, the onboard temp sensor shows an incorrect temperature value (-52 ° C). How can I solve this problem?
You did not restart your remote measuring and monitoring device after the firmware update. Under "System Menu" you will find the Point "Reboot the system". Please click on it and restart your environmental monitor. Please close your web browser and empty the cache. After a few seconds, you can log in again. The onboard temperature sensor will now display the correct value.